Two (2) units’ single stage back pressure turbine coupled to alternator, output
1.200 kW. The installation turbine by contractor.
Make : SHINKO, Dresser-Rand or equivalent.
Main steam separator.
Steam pipes from steam separator to steam turbine and condensate pipe c/w
necessary one (1) individual steam separators, valves and fitting would be supplied and installed.
A return line pipe ex. cooling of turbine c/w fitting to water settling basin.
Speed : 5,400 rpm
Inlet Pressure : 22 barg
Inlet Temperature : 219.6o C
Exhaust Pressure : 3.2 barg
Steam Rate : 2.63 kgs/kwh
Steam Flow : 27,156 kgs/hr